Depending on the generator type, the default parameters of the PID may not be suitable for LVRT events and tests.
The duration of the response time after the fault is related to the PF/kVAR regulation loop. In order to improve, you can:
- Increase the proportional part of the PID ( e.g 5 times higher)
- If this is still not enough, increase the Integral part