As shown on the figure above the reactive power drops dramatically after 1 second. this is a consequence of excitation drop. The AVR in this situation detects a loss of sensing and then turns down the excitation current to its shutdown value.
To avoid this malfunction, it is recommended to disable the loss of sensing protection.
Note: LVRT = Low voltage ride through